Product standard: GB5023.3.6-2008(IEC227-6:1985) and CNCA-01C-002:2007
Model: TVVB, TVVB (G)
Cable Specification: TVVB 300/500V 0.75~1.0mm2 (25-60) cores; TVVB (G) 300/500V 0.75~1.0mm2 (25-60) cores
Operating Temperature: -0°C~40°C (Max. allowed temperature of conductor is 70°C)
Conductor Class: Class 5
Conductor Material of Elevator Travel Cable: Anaerobic soft copper wires
Insulation Material: High quality lead-free PVC soft insulation material
Color of Insulation Core: Various colors with printed numbers
Sheath Material and Color: High quality cold proof and lead-free elastic PVC, gray (or black)
Burning Test: Conforms to the requirements for single cable vertical burning test specified by IEC60332-1.
DC Resistance of Conductor at 20°C: Complies with GB3956.-1997(IEC228:1978) and JB8734.3~4-1998
Insulation Resistance at 70°C: Complies with GB5023.3-2008 (idt IEC227-3:1985)
Finished Product Voltage Withstand Test: 300/500V: 2.0KV(AC)/5min, no breakdown
Mechanical Specification of Finished TVVB Flexible Elevator Cable:
Free suspension length: ≤80m；
Travel height: ≤160m；
rated speed: ≤4.0m/s;
Free bending diameter: ≤700mm;
Minimum bending diameter: 8 times of cable thickness;
Flexibility test＞3,000,000 times (No broken circuit or short circuit occurs to the insulation core.)
Product Certificate: 3C certificate No.: 2004010105119789; CE Certificate No.: CE-LVD-0502
Lead Free Environmental Performance: The content of heavy metal element in our flexible cable for elevator fully complies with EU RoHS specification.
京海彩票 note: when the rated speed is in the range of 4.0m/s-10.0m/s and the free suspension length exceeds 80m, the flexible cable should be added with reinforced component made of galvanized steel wire or fiber wire. the corresponding cable model is tvv (g).
京海彩票1. make sure all the equipment inside the control panel cabinet is connected to earth properly. the short and thick earth wire should be connected to the suitable earth point or earth busbar. 2. the sheathed customized elevator cable usually uses flat conductor (such as metal mesh) which has low impedance under high frequency power transmission. 3. the power cable must be shielded in order to restrain the radiation and transmission of electromagnetic wave. at the same time, transfer impedance of the shield layer needs to be taken into consideration.
京海彩票burning test: conforms to the requirements for single cable vertical burning test specified by iec60332-1. dc resistance of conductor at 20°c: complies with gb/t3956-1997 (iec228) and jb8734.5-1998 insulation resistance at 70°c: complies with gb5023.7-2008 (iec227-7) and jb8734.5-1998